2011 Back Issues
27th Edition of Performance Specs
Volume 41 No. 1
Simple Cycle Design Ratings
OEM design performance specifications for more than 200 gas turbines in production for 50/60-Hz electric power and cogeneration operation.
Update by GTW editors, pp 11-21.
Mechanical Drive Design Ratings
OEM design performance specifications for aero and industrial gas turbines in production for oil, gas, LNG and petrochemical project operation.
Update by GTW editors, pp 23-28.
Combined Cycle Design Ratings
OEM reference plant design performance specifications for optimized 50/60-Hz combined cycle power blocks with unfired HRSGs.
Update by GTW editors, pp 31-40.
Marine Propulsion Design Ratings
OEM design performance specifications for marinized gas turbine engines in production for electric motor, waterjet and propeller shaft propulsion.
Update by GTW editors, pp 41-43.
Volume 41 No. 2
New industrial design series
covering 6 to 10MW range
Design features and performance of MAN industrial frame unit rated at 6630kWe and 32.0% efficiency with less than 25 ppm NOx over wide range of full to part-load output.
By Junior Isles, pp 8-11.
Moroccan 315MW plant de-rated
for daily cycling on heavy fuel oil
Three 127.6MW simple cycle gensets are being de-rated to run on No. 6 fuel oil at 105MW base load each and 31.8% efficiency at less than 2000°F firing temperature.
By Robert Farmer, pp 12-15.
Optical sensors being developed
to survive extremely high temps
Gas turbine combustor section optical technology sensors that have endured several hundred hours of operation at around 500°C are now being tested at over 1000°C.
By Ian Macafee, pp 16-18.
What suppliers are doing to lower
HPT replacement components cost
Large non-OEM supplier is improving on refurbishment techniques to reduce scrap rates and guaranteeing repaired vanes and blades rather than provide new spare parts.
By Bill Owen, pp 20-22.
Volume 41 No. 3
Gas turbine’s new role reflects
developing global energy shifts
Economic, regulatory and technical developments behind growing shift in the US (and world) away from coal steam plants to natural gas fired gas turbine power generation, backed up by charts, curves and tables.
By Harry Jaeger and Bill Owen, pp 10-18.
Background and likely future of gas
turbine power in the US and world
Political, technical and industry events going back to the 1965 blackout that have shaped the volitle growth and contraction of gas turbine utilization and what the future portends.
By Harry Jaeger and Bill Owen, pp 19-23.
Chemical looping combustion for
high efficiency and carbon capture
Long range “silver bullet” under study with the potential to combine inherent CO2 capture with efficiencies well beyond today’s most advanced combined cycles.
By Prof. Peter Childs, pp 24-27.
20-yr old 474MW combined cycle
converted to a ‘new’ 526MW plant
After 20 years of on-off cyclic duty, combined cycle plant powered by four GT11Ns is now rated at 526MW net output and 50.0% efficiency from 474MW and 47.3% efficiency.
By Robert Farmer, pp 28-31.
Volume 41 No. 4
Validation tests of 50Hz 8000H
plant confirm 60.75% efficiency
Project engineers report the plant has achieved a net base load output of 578MW, ramp rates of 15 to 35MW per minute, less than 30-minute hot startups from zero to full load.
By Junior Isles, pp 14-17.
Flex 50 design rated over 61%
net combined cycle efficiency
New 50Hz 9FB plant is design rated at 510MW net output, hot startup from zero to full load in less than 30 minutes, 50MW per minute ramp rate, and over 40% turndown.
By Junior Isles, pp 18-21.
New GT26 core of 500MW+ KA26
CC plant with over 61% efficiency
Next generation 50Hz KA26 combined cycle plant will deliver over 350MW within 15 minutes of startup, full output in less than 30 minutes, and high part-load efficiencies.
By Junior Isles, pp 22-25.
Frame 6B flange-to-flange upgrade
boosts efficiency by over 8 per cent
Upgrade of 1992 Fr 6B during major overhaul has added 4600kW to power output, raised simple cycle efficiency to 31.6% and prolonged its service life by 25 years.
By Mike Forish, pp 26-28.
Volume 41 No. 5
New GT24 gas turbine design for
advanced flexible 60Hz CC plant
Optimized two-on-one KA24 combined cycle with upgraded GT24 can idle at 20% part-load and ramp up to deliver over 450MW of spinning reserve capacity within 10 minutes of dispatch.
By Junior Isles, pp 12-16.
Ultra-low DLE breakthrough for
small 8 to 10MW sized gas turbines
Single-digit dry low emissions technology will debut on an upgraded M7A gas turbine rated at 7.8MW and 34.1% efficiency with less than 9 ppm NOx and 25 ppm CO over a 50 to 100% load range.
By Robert Farmer, pp 18-20.
1510MW oasis of power at water
desalination complex in AbuDhabi
Site-rated 1510MW plant is built around two SCC5-4000F 2x1 combined cycle power blocks ISO rated at 832MW net output and 58.5% net plant efficiency each.
By Tim Probert, pp 22-26.
1.8MW gensets at remote site running
for over 50,000 hrs without overhaul
Two sets are running on corrosive wellhead gas well past prescribed 40,000-hr major overhaul to provide 24/7 base load power with waste heat recovery for arctic site.
By Robert Farmer, pp 28-32.
Volume 41 No. 5
Carbon capture ready designs
call for more than extra space
Competing post-combustion technologies for combined cycle plant operation are under development and test, but the cost of energy losses for carbon capture remain prohibitive.
By Tim Probert, pp 12-15.
Combined cycle repowering
adds 30MW to RB211 plant
Two 28MW RB211s in simple cycle base load service on Batam Island since 2004 have been converted to a 2x1 combined cycle plant rated at 85MW and 52.8% efficiency.
By Robert Farmer, pp 16-19.
LaCaridad combined cycle
project to save 4¢ per kWh
Two SSC6-5000F combined cycles being built in Mexico, each rated 250MW and 56.9% efficiency, will reduce COE for mining operations to 6¢ per kWh from current 10¢ level.
By Junior Isles, pp 20-22.
PGT25+ compressor station
utilizing exhaust for power
Organic fluid-vapor expander gensets operating off hot gas turbine exhaust will each generate 7.9MW for sale to regional utilities under long term power purchase agreements.
By Robert Farmer, pp 24-26.
Moveable power barge rated
125MW and 41% efficiency
Shallow draft power barge serves as a floating power house for two Trent 60 gensets to supply backup or interim power pending the completion of new plants in remote regions.
By Junior Isles, pp 27-30.
Gas Turbine World
PO Box 447
Southport, CT 06890 USA
© 2017 Pequot Publishing Inc. All rights reserved.
Reproduction without written permission strictly prohibited.